The plant to be described is to produce 500 MW of electrical power. The flow rates, compositions, stream conditions, and other details to be given are representative of such installations. The key step in removing SO2 from the stack gas is the reaction of SO2 with CaO and oxygen to produce CaSO4 , an insoluble stable compound. Four major components of the process will be traced: the coal‐limestone‐stack gas streams, the scrubber water, the cooling‐heating water cycle, and the generated steam cycle.
The composition of coal can vary considerably, but that shown in Table CS 2.1 is typical of that used in this process. During coal combustion the sulfur in the coal reacts to form SO2 and very small amounts of SO3 . Eighty‐five percent of the ash in the coal leaves the boiler in the stack gas as fly ash; nitrogen emerges as N2 , and the carbon, hydrogen, and sulfur in the fuel are oxidized completely to CO2 , H2O, and SO2 .
Finely ground limestone, whose composition is given in Table CS 2.2, is injected directly into the furnace where complete calcination occurs. 2
The limestone feed rate to the furnace is 10% in excess of that required for complete consumption of the generated SO2 . Both limestone and coal enter the process at about 77°F. A waste stream consisting of 15% of the limestone inerts and coal ash is removed from the furnace at 1650°F.
Air at 110°F and 30% relative humidity is brought to 610°F in an air preheater, and the heated air is fed to the furnace. The air feed rate is 40% in excess of that required to burn the coal completely. Gases from the furnace containing fly ash, CaO, and CaSO4 and at 890°F are cooled in the air preheater and then split into three trains. The gas in each train is cooled further to 177°F, and fed to a scrubber where it is contacted with an aqueous slurry of CaO and CaSO4 . Sulfur dioxide is absorbed in the slurry and reacts with the CaO. The gas leaving each scrubber contains 3.333% of the SO2 and 0.3% of the fly ash emitted from the boiler furnace. The effluent gas from the scrubber, which is at 120°F and saturated with water, is heated and mixed with the gas streams from the other trains. The combined gas stream is sent to a blower where its pressure is increased from 13.3 psia to 14.8 psia; it is then exhausted through a stack to the atmosphere.
The liquid feed enters the scrubber at 117°F and contains 10.00 wt% solids; it is fed at a rate such that there are 6.12 lbm liquid per lbm inlet gas. Liquid scrubber effluent at 120°F is sent to a holding tank where it is mixed with fresh makeup water and water recycled from a settling pond. From the holding tank, one stream is recycled to serve as liquid feed to the scrubber and another is pumped to the settling pond for solids removal.
Generation of steam and its utilization in the production of electricity in this plant is typical of many power cycles. Steam is generated in the boiler and leaves the boiler and superheater tubes at 1400°F and 2700 psia. It is expanded through a turbine where its pressure and temperature are reduced to 5 psia and 200°F. The low‐pressure steam is then condensed at constant pressure and pumped isothermally to the inlet boiler tubes.
The temperature of the water used to cool the gas entering the scrubber is 148°F. The hot water at 425°F is then used to reheat the effluent gas stream from the scrubber. (The water thus undergoes a closed cycle.)
The power company for which you work is contemplating adding an SO2 scrubber to one of its generation stations and has asked you to do the preliminary process evaluation. In solving the following problems, you may neglect the formation of SO3 in the furnace, and assume that CaSO4 and CaO are the only calcium compounds present in the slurry used in the scrubber (i.e., neglect the sulfite, bisulfite, and bisulfate compounds that are present to some extent in the real process).
Delivering a high-quality product at a reasonable price is not enough anymore.
That’s why we have developed 5 beneficial guarantees that will make your experience with our service enjoyable, easy, and safe.
You have to be 100% sure of the quality of your product to give a money-back guarantee. This describes us perfectly. Make sure that this guarantee is totally transparent.Read more
Each paper is composed from scratch, according to your instructions. It is then checked by our plagiarism-detection software. There is no gap where plagiarism could squeeze in.Read more
Thanks to our free revisions, there is no way for you to be unsatisfied. We will work on your paper until you are completely happy with the result.Read more
Your email is safe, as we store it according to international data protection rules. Your bank details are secure, as we use only reliable payment systems.Read more
By sending us your money, you buy the service we provide. Check out our terms and conditions if you prefer business talks to be laid out in official language.Read more